Order Onine at DrinkingFountainDoctor.com
Halsey Taylor HRFSER-Q Contour Water Cooler
$46.50 Freight Shipping
The HRFSER-Q Water Cooler is a bi-level unit with front push buttons, the higher unit is on the left. The refrigerated drinking fountain meets child and adult ADA requirements. A chiller is recessed within the wall behind the louvered ventilating grill.
Features and Beneifts
Face-mounted, one-piece, non-corrosive stainless steel cooler top, number 300 series with satin finish, contour-formed basin with softly rounded corners.
Exclusive one-piece, chrome-plated two-stream mound-building bubbler with non-removable anti-squirt feature and integral hood insures a satisfying drink of water.
Push Button Actuation Mechanism
Self-closing, vandal-resistant push-button does not require grasping or twisting.
Automatic Stream Height Regulator
Self-closing assembly is located inside unit to prevent tampering. Unit resists corrosion and liming. A constant stream height is automatically maintained under line pressures that vary from 20 to 105 psi.
Easily cleaned in-line strainer screen traps particles of 140 microns or larger before they enter the waterway.
Mounting frame is manufactured of corrosion resistant, galvanized steel. Open construction designed for ease of installation. Mounting frame can be shipped in advance for rough-in installation.
Constructed of stainless steel, number 300 series with satin finish. Removable lower panel providing access to plumbing and refrigeration system. Panels overlap wall opening 1/2”.
Hermetically sealed, positive start compressor with lifetime lubrication and built-in overload protection, efficient capillary sizing, large capacity dryer-strainer, and self-lubricated fan cools copper/aluminum condenser. System uses R134A refrigerant. Protected by Halsey Taylor’s Limited 5 Year Warranty.
Shall deliver 7.5 GPH of 50° F water at 90° F ambient and 80° F inlet water. Fountain shall include push-button valve on front, contour-formed basin to eliminate splashing and standing water, and rounded corners and edges. Bubbler shall be chrome plated, two-stream, mound- building type. Cooling unit shall have a high efficiency positive start compressor using R134A, with pressurized counter-flow cooling evaporator/chiller. Cooler shall comply with ANSI 117:1 and ADA for visual and motion disabilities. The manufacturer shall certify the unit to meet the requirements of NSF/ANSI 61, and the Safe Drinking Water Act. Unit complies with ARI Standard 1010.