Order Onine at DrinkingFountainDoctor.com
Halsey Taylor BFMR-Q Recessed Water Cooler
$46.50 Freight Shipping
The BFMR Series is Halsey Taylor’s fully recessed drinking fountain line designed for uninterrupted corridor space. BFMR drinking fountains are ADA-compliant and have a cooling unit (chiller) recessed within the wall behind the louvered ventilating grill.
The BFMR-Q Water Cooler has a front push button.
Features and Beneifts
One-piece, non-corrosive stainless steel cooler top, number 300 series with satin finish and contour-formed basin.
Exclusive one-piece, chrome-plated two-stream mound-building bubbler with non-removable anti-squirt feature and integral hood insures a satisfying drink of water.
Push Button Actuation Mechanism
Self closing, vandal-resistant push-button does not require grasping or twisting.
Automatic Stream Height Regulator
Self-closing assembly is located inside unit to prevent tampering. Unit resists corrosion and liming. A constant stream height is automatically maintained under line pressures that vary from 20 to 105 psi.
Easily cleaned in-line strainer screen traps particles of 140 microns or larger before they enter the waterway.
Mounting frame is manufactured of corrosion resistant, galvanized steel. Open construction designed for ease of installation. Mounting frame can be shipped in advance for rough-in installation.
Cabinet and Access Panel
Cooling unit contained in a heavy gauge galvanized steel cabinet with front and rear panels removable for service. The upper louvered panel is easily removable for access to the chiller unit system.
Hermetically sealed, positive start compressor with lifetime lubrication and built-in overload protection, efficient capillary sizing, large capacity dryer-strainer, and self-lubricated fan cools copper/aluminum condenser. System uses R134A refrigerant. Protected by Halsey Taylor’s Limited 5 Year Warranty.
Shall deliver 8 GPH of 50° F water at 90° F ambient and 80° F inlet water. Fountain shall include push-button valve on front, contour-formed basin to eliminate splashing and standing water. Bubbler shall be chrome plated, two-stream, mound-building type. Cooling unit shall have a high efficiency positive start compressor using R134A, with pressurized counter-flow cooling evaporator/chiller. Cooler shall comply with ANSI 117:1 and ADA for visual and motion disabilities. The manufacturer shall certify the unit to meet the requirements of NSF/ANSI 61, and the Safe Drinking Water Act. Unit complies with ARI Standard 1010.