Order Onine at DrinkingFountainDoctor.com
Halsey Taylor SJ19-Q Remote Chiller 19 GPH
$46.50 Freight Shipping
Halsey Taylor Remote Chillers can convert a non-refrigerated drinking fountain into a refrigerated drinking fountain. The units can also be connected to a bubbler, glass filler, or cold water dispenser. The SJ19-Q Remote Chiller is a powerful remote chiller. It is a 19 GPH (gallons per hour) unit.
Features and Beneifts
Manufactured of rust-resistant heavy gauge galvanized steel. Removable service panels.
3/8” O.D. inlet and outlet.
7/8” diameter opening for conduit connection.
Cooling Coil and Storage Tank
Combination tube/tank type. Tube portion is continuous coil of copper-tubing.
Unit bearing self-lubricating type for maintenance-free longer life.
Copper/aluminum construction with associated shroud
Thermostat for cooling and storage tank is factory set for 50° F water. Adjustable ± 5° F.
Furnished with 6” leads enclosed in junction box for direct connection to standard 115 volt, 60 Hz, single phase.
Hermetically sealed, positive start compressor with lifetime lubrication and built-in overload protection, efficient capillary sizing, large capacity dryer-strainer, and self-lubricated fan cools copper/aluminum condenser. System uses R134A refrigerant. Test pressures, highside 325 psig., lowside 140 psig. Protected by Halsey Taylor’s Limited 5 Year Warranty.
It is important to insure proper ventilation. Allow a minimum clearance of 12” (305mm) in the front and 3” (76mm) in the rear of the unit. If unit is to be installed in an enclosure, allow the following clearances around unit: 1 inch (25mm) on each side, 3 inches (76mm) in the rear and 3 inches (76mm) inches above wall.
Shall deliver 19 GPH of 50°F water at 90°F ambient and 80°F inlet water. Designed for use with any drinking fountain. Compressor shall be hermetically sealed. Manufacturer shall certify unit to be lead free as defined by the Safe Drinking Water Act. System controlled by adjustable thermostat. Complies with ARI Standard 1010.
SJ19 can serve 3 fountains.
Locate chiller within 15 feet of fountain for optimum performance.